Enumerated values 0-63 are reserved for prototype by ASHRAE. Enumerated values 64-255 may be used by others subject to the procedures and constraints described in Clause 23.
Enumerated values 0-63 are reserved for prototype by ASHRAE. Enumerated values 64-65535 may be used by others subject to the procedures and constraints described in Clause 23.
Enumerated values 128-511 are used for events which indicate that access has been denied. Enumerated values 0-511 are reserved for prototype by ASHRAE. Enumerated values 512-65535 may be used by others subject to the procedures and constraints described in Clause 23.
Other services to be added as they are defined. All enumeration values in this production are reserved for prototype by ASHRAE. Proprietary extensions are made by using the ConfirmedPrivateTransfer or UnconfirmedPrivateTransfer services. See Clause 23
Enumerated values 0-255 are reserved for prototype by ASHRAE. Enumerated values 256-65535 may be used by others subject to the procedures and constraints described in Clause 23.
Enumerated values 0-63 are reserved for prototype by ASHRAE. Enumerated values 64-65535 may be used by others subject to the procedures and constraints described in Clause 23. The last enumeration used in this version is 5.
-- Enumerated values 0-63 are reserved for prototype by ASHRAE. Enumerated values 64-65535 may be used by others subject to the procedures and constraints described in Clause 23. It is expected that these enumerated values will correspond to the use of the complex-event-type CHOICE [6] of the BACnetNotificationParameters production.
Enumerated values 0-255 are reserved for prototype by ASHRAE. Enumerated values 256-65535 may be used by others subject to procedures and constraints described in Clause 23.
Enumerated values 0-63 are reserved for prototype by ASHRAE. Enumerated values 64-65535 may be used by others subject to procedures and constraints described in Clause 23.
Enumerated values 0-127 are reserved for prototype by ASHRAE. Enumerated values 128-1023 may be used by others subject to the procedures and constraints described in Clause 23.
The special property identifiers all, optional, and required are reserved for use in the ReadPropertyMultiple service or services not defined in this standard. Enumerated values 0-511 are reserved for prototype by ASHRAE. Enumerated values 512-4194303 may be used by others subject to the procedures and constraints described in Clause 23.
Other services to be added as they are defined. All choice values in this production are reserved for prototype by ASHRAE. Proprietary extensions are made by using the UnconfirmedPrivateTransfer service. See Clause 23
used only with array datatype if omitted with an array the entire array is referenced
any datatype appropriate for the specified property
UTC time, all wild if unknown
0 if key set is not configured
first octet: month (1..14), 1 =January, 13 = odd months, 14 = even months, X'FF' = any month; second octet: weekOfMonth where: 1 = days numbered 1-7, 2 = days numbered 8-14, 3 = days numbered 15-21, 4 = days numbered 22-28, 5 = days numbered 29-31, 6 = last 7 days of this month, X'FF' = any week of this month; third octet: dayOfWeek (1..7) where 1 = Monday... 7 = Sunday, X'FF' = any day of week
used only when property is commandable
used only with array datatype
shall be present if Bacnet/IP, and absent for BACnet/IPv6
used only with monitored properties with a numeric datatype
only if segmented messages
as per 20.1.2.5
as per 20.1.2.4
Other services will be added as they are defined. All choice values in this production are reserved for prototype by ASHRAE. Proprietary extensions are made by using the ConfirmedPrivateTransfer service. See Clause 23.
CHOICE [6] has been intentionally omitted. It parallels the complex-event-type CHOICE [6] of the BACnetNotificationParameters production which was introduced to allow the addition of proprietary event algorithms whose event parameters are not necessarily network-visible. CHOICE [19] has been intentionally omitted. It parallels the change-of-reliability event type CHOICE[19] of the BACnetNotificationParameters production which was introduced for the notification of event state changes to FAULT and from FAULT, which does not have event parameters.
time to live in seconds at time of registration
the 6-octet B/IP or 18-octet B/IPv6 address of the registrant
remaining time to live in seconds, incl. grace period
4 octets for B/IP, or 16 octets for B/IPv6
Internet host name (see RFC 1123)
depends on referenced property
depends on ref property
used only with array datatype; if omitted with an array then the entire array is referenced
used only with array datatype; if omitted with an array the entire array is referenced
used only if 'Item Count' > 0 and the request was either of type 'By Sequence Number' or 'By Time'
used only with array datatypes
present only if all-new-data-accepted = false
must be used as a pair, see 16.10
to be present if locationSpecifier has the value 'specified'
to be present if timeRangeSpecifier has the value 'specified'
see Clause 20.2.12 for restrictions
Optionally limited to 32 bits
CHOICE [20] has been intentionally omitted. It parallels the 'none' event type CHOICE[20] of the BACnetEventParameter production which was introduced for the case an object does not apply an event algorithm
any primitive datatype; complex types cannot be decoded
Note that the combination of level, ramp-rate, step-increment, and fade-time fields is dependent on the specific lighting operation. See Table 12-67
This production represents the possible datatypes for properties that have discrete or enumerated values. The choice must be consistent with the datatype of the property referenced in the Event Enrollment Object. Tag values 0-63 are reserved for prototype by ASHRAE. Tag values of 64-254 may be used by others to accommodate vendor specific properties that have discrete or enumerated values, subject to the constraints described in Clause 23.
for encoding of values into this octet string see ANNEX P
A value of 0 indicates the local network
A string of length 0 indicates a broadcast
used only with array datatypes; if omitted with an array the entire array is referenced
used only with array datatype if omitted with an array then the entire array is referenced
NOTE: The valid combinations of error-class and error-code are defined in Clause 18.
Other services to be added as they are defined. All choice values in this production are reserved for prototype by ASHRAE. See Clause 23.
%Enumerated values 0-63 are reserved for prototype by ASHRAE. Enumerated values 64-65535 may be used by others subject to the procedures and constraints described in Clause 23
value is limited to primitve datatypes and BACnetDateTime